Replacement air damper Power Open with 120Vac plug-in vent fan and dampers controlled by vent switch
HMI Hoyme Manufacturing Inc. Special Note: Circuits are colored for clarification only and are not necessarily those found in actual installations.
Diagram #8A3: Forced Air Furnace having a combustion air supply duct that also serves as a combustion air supply for a 120Vac gas dryer as a second appliance.
2. 24Vac Relay Adaptor with a Duplex Receptacle and a Red Light on/off Switch (RADP-0241-S10A) to function as a control centre interlocked to120Vac supply for a plug-in type Gas Dryer.
1. Combustion Air Damper is interlocked to open for furnace firing and/or to open for dryer operation.
2. The Gas Dryer is plugged into the RADP-0241-S10A receptacle and will operate only after the Red Light Switch is turned on and the Combustion Air Damper is in the open position. When the dryer has completed its cycle, the Adaptor Red Light Switch is to be turned off allowing the combustion air damper to close.
Note: Manual setting of the furnace fan does not affect the Combustion Air Damper operation.
This installation does not interfere with the operation of the Air Conditioner.
1222-ld - Printed in Canada
Printer friendly (pdf) - (Opens in a new window)
Last Updated (Friday, 09 November 2012 16:12)